By Giorgio Lorenzetti, Technical Manager at MITA Cooling Technologies
Most industrial plants also include various types of cooling systems in addition to the actual production part: evaporative towers or condensers, dry coolers, adiabatic coolers, chillers, etc. In some cases, this equipment must comply with stringent noise limits, especially in relation to their power and size.
Current technology enables us to achieve optimal sound levels: therefore, it is essential to know the calculation criteria well.
The systems specified above have a well-defined dimensional mass calculation: this way the sound power level must also take into account the emission surface of the equipment itself.
European standard EN ISO 3744 specifies the criterion to use to calculate the sound power level of machinery with measurable dimensions “X, Y, Z”. According to this standard, a series of sound pressure measurements must be performed at points with equivalent distances from the equipment: thus a weighted average is obtained; then the logarithm of the surface of the same equipment has to be added to this average. As a result, we get the calculated sound power level.
The sound power data of the equipment thus calculated can be useful to Customers or Consultants to forecast the acoustic impact of new installations. The presence of background noise, possible obstacles or reflective walls, and the noise produced by other machinery in the surrounding area must be taken into account in this measurement.
The sound pressure value at a certain distance is frequently requested to manufacturers. The value could be incorrectly interpreted. In fact, the standard specifies that the equipment to calculate the sound power level must be installed “on a flat reflecting plane in an environment that approximates to an acoustic free field”: therefore, it is clear that any sound pressure value supplied cannot be found in a condition different from that calculated theoretically.
Here are some cases that a trained technician must be able to deal with.
All these interpretative variables lead to differences, which can be significant when the Manufacturer must provide a noise value consistent with reality.
As already mentioned, the sound and correct practice would be to supply the sound power level of the equipment calculated according to EN ISO 3744; then, this value is to be used to derive the impact that it can determine once the machine is placed in the installation site.